top of page
METHOD OF PROTECTING A PLASTIC PIPE WITHOUT INSULATION PENETRATING A RIGID FLOOR ACCORDING TO ETA-17/1064
1 - rigid floor with thickness B ≥ 150 mm
2 - plastic pipe, diameter "D" and pipe wall thickness "t" (see Annexes B and D)
3 - Piro Wrap PW with dimensions [h x s] mm; placed at the
distance l = 10 mm from the underside of the floor
4 - space between the pipe and the floor structure, width u = max.
25 mm, filled with cement mortar
Technical drawing 1
Steps 1 - 5
Read in the table pipe diameter and select the appropriate size of Piro Wrap PW.
Wrap around the pipe and secure the wrap with the integrated adhesive.
Slide the secured wrap into the partition. Location of the wrap inside the hole - 15 ± 5 mm from the bottom of the floor.
Mark the completed penetration seal with the attached label, mark Piro Wrap PW on it, enter the date and name.
bottom of page