top of page
METHOD OF PROTECTING A PLASTIC PIPE WITHOUT INSULATION WITH CABLE BUNDLES INSIDE ACCORDING TO ETA-17/1061
1 - flexible or rigid wall with a thickness of B = min. 100 mm
2 - plastic pipe, diameter "D" and pipe wall thickness "t"; with a bundle of cables inside, with a diameter of 60 mm, consisting of a maximum of 5 cables with a diameter not greater than 13 mm
3 - Piro MULTITUBE PM with dimensions [h x s] placed centrally inside the wall
4 - cable tie or adhesive tape
5 - the gap between the pipe and the partition, width "a", filled mineral wool with a density
of min. 60 kg/m3
6 - gypsum mortar with a thickness of g1 = min. 5 mm
Technical drawing 1
Steps 1 - 5
Place EPipe in the hole so that its black part is centrally located inside the partition.
Fill the empty space between the partition and the duct with cement mortar.
Cut off the parts of EPipe on both sides of the partition by means of saw.
Run cables inside the duct (cables should cover no more than 60% of the duct fill).
Plug the remaining free space of the duct with the provided plugs.
bottom of page