top of page
METHOD OF PROTECTING A PLASTIC PIPE WITHOUT INSULATION PENETRATING A RIGID WALL ACCORDING TO ETA-17/1063
1 - rigid wall thickness B = min. 100 mm
2 - plastic pipe, diameter "D" and wall thickness "t" space between pipe insulation and wall structure width u = max. 15 mm, filled with gypsum plaster to a depth of min. 10 mm
3 - Piro Collar PC SLIM mounted on both sides of the wall
4 - fire collar mounting - steel expansion anchor bolt M6x60 or M8x80
Fill the space between the pipe wall and the partition tightly. Use cement mortar.
Steps 1 - 5
Remove the securing pin and place the fire collar on the pipe
Pull the locking pin of the clamp through the fixing slot on the other end of the collar and fold it 180° backwards so that the collar is firmly closed on the pipe.
Attach fire collar to the wall with expansion anchor bolts. Do not use expansion anchor bolts containing plastic elements.
Mark the completed penetration seal with the label attached to the set. Mark Piro Collar PC on it, enter the date and the name.
bottom of page